If you own a business, fire extinguisher inspection is a vital part of keeping your business safe. The NFPA 10 Standard for Fire Extinguishers outlines the process for regularly inspecting fire extinguishers. The NFPA 10 requires inspections every six months. If the fire extinguishers are used in the workplace, they should be inspected every other month. However, if you’re not sure when your company should schedule an inspection, check the NFPA 10-mandated schedule for fire extinguisher maintenance.
When performing a fire extinguisher inspection, you should first check the pull-pin and the tamper-seal to ensure that both are intact. The fire extinguisher inspection tag should also be present. The tag should state that the last annual inspection was performed within the past year. Visually inspect the fire hose to make sure that it’s in good condition and that it’s free from cracks or damage. If you notice debris or other signs of trouble, then it’s time to replace the extinguisher.
After completing a fire extinguisher inspection, you should check the safety pin. It should not be loose, and the gauge needle should point towards the green area. Once the safety pin is tightened, you can pick up the fire extinguisher and see if it’s empty or full. If it’s damaged, you should replace it with a new one. There are a few ways to check if your fire-extinguisher is safe and ready for use.
The discharge lever should be able to close with ease, and its needle should point towards the green area. If the needle is in the red zone, the extinguisher needs to be recharged or replaced. During a fire-extinguisher inspection, the needle should remain in the green zone. Otherwise, the extinguisher needs to receive an annual inspection. You should also look at the safety pin’s safety pin to ensure that there is no unwanted discharge during the process.
The fire-extinguisher must be checked periodically for the right operation. The pull-pin and the tamper seal should be in good shape. The serial number and instructions for the correct use should be legible. The hose should be free of cracks and leaks. The locking pin should pass through the holes in the neck. When in doubt, you should call a professional to perform the inspection.
It is essential to regularly inspect the fire-extinguisher. The safety pin should be intact. The fire extinguisher should be in good physical condition. Its label should be legible and have the serial number and instructions for use. Moreover, the cylinder and hose should be free of damages. The nozzle should also be free of clogs and debris. It should be plugged in the fire-extinguisher’s holder.
A fire-extinguisher should be in good physical condition. It should have a legible label and the serial number. The nozzle should be free of damage. The cylinder should be free from cracks and leaks. The locking pin should also pass through the holes. A well-maintained fire-extinguisher should have an inspection tag. If the tether is missing, you must replace it.
It is important to check the extinguisher’s hose. It should not be cracked or brittle. The gauge should be in the green zone. If it is off, it means it has been used. The needle should be in the red zone if it is overcharged. The inspection tag should be on the canister’s neck and gauge. The pin should not be corroded and it should be inserted in the hole where it should be.
If a fire extinguisher is not in good physical condition, it should be checked by a professional. It should have a clear label with the serial number and instructions on how to use it. It should also have no rust or cracks on the nozzle. The lock should also pass through the holes where the locking pin should go. The tagging should be visible to everyone in the house.
When it’s time to check your fire extinguisher, make sure it’s properly set up. There should be no obstructions in the way. The pull pin should be tightened securely and be clearly labeled. The tamper seal should be intact. The instruction label should be legible. If there are any cracks or dents, you should get them repaired or replaced.